Convert Ungrounded to Resistance-Grounded Systems
Resistance grounding protects a system against transient overvoltages caused by intermittent ground faults and it provides a method to locate Ground Faults. (Transient overvoltages and inability to locate ground faults are the most common safety issues with ungrounded systems.)
Conversion of delta-connected or wye-connected sources with inaccessible neutrals require a zigzag transformer to derive an accessible neutral for connection to a neutral grounding resistor (NGR). The neutral is only used for the NGR and not for distribution. During normal operation the only current that flows in the zigzag transformer is an extremely small magnetizing current. When one phase is grounded, the NGR and the zigzag transformer provide a path for ground-fault current to flow.
Design Note 1: A zigzag conversion requires a three-phase connection to the existing power system, typically at the main transformer or switchgear. See Figure 1.
Design Note 2: The resistor let-through current must be greater than the system capacitive charging current.
Design Note 3: Protection, coordination, and annunciation systems depend on the integrity of the NGR. NGR monitoring with an SE-330 or SE-325 is recommended.